Installation, Configuration and Operation of Hardware > Installation and Configuration of Additional Devices > Hanwell SMS Module >> Hanwell IceSpy SMS Module Relay Connectors
•Pins 1 and 3, 2 and 4, 5 and 6 are internally connected together in pairs to increase the current carrying capacity. See Figure 198 above.
•The shield wire is internally connected to GND. See Figure 198 above.
•Both relays have the same pinout and the cables are interchangeable.
•These relay outputs are suitable for low voltage switching.
Rating: Maximum Load 1A at 24V.
DO NOT exceed 50V.
Shield is connected to Unit's 0V rail.