Installation, Configuration and Operation of Hardware > Installation and Configuration of Control Devices > Hanwell IceSpy Network Receiver >> Hanwell IceSpy Network Receiver Relay Connections
•Pins 1 & 3, 2 & 4 and 5 & 6 are connected together internally in pairs to increase the relay’s current carrying capacity. See Figure 173 above.
•The Shield wire is internally connected to Ground (GND).
•Both relays (1 and 2) have the same pinout and the cables are interchangeable.
•These relay outputs are suitable for low voltage switching.
Rating: Maximum Load 1A at 24V.
DO NOT exceed 50V.
Shield is connected to Unit's 0V rail.